This SCADA RTU panel example is designed to mount inside a heated Pump Station Building. It s primary function is being a Pump Station Control Panel with a redundant (Radio, Autodialer) communications interface back to the central monitoring system.
Our customer develops and maintains municipal water facilities. They used to get competitive quotes for each new project. This was the norm for years to promote competition and reduce panel cost, yet it increased total costs.
Each new panel shop created new problems. Our customer issued a Request For Proposal (RFP) to legitimize their selection of a preferred panel shop. They selected us and now specify us the control panel manufacturer.
Engineering Submittal Package
We produce an engineering submittal package for every control panel we’re planning to produce. We submit to our customer for review and approval prior to releasing it to production. This allows everyone to review what we’re planning to produce and confirm that it’s correct. Each includes the following sections.
- Section A. Datasheets for Enclosures and Accessories
- Section B. Datasheets for Power and Control Devices
- Section C. Datasheets for Field Mounted Devices
- Section D. Drawings
- Section E. Bill of Material
Click here to see our SCADA RTU Panel Submittal
|Safety Certification Label||UL508A|
|Enclosure Type||Floor Mount||Wall Mount if small enough|
|Enclosure Material||Steel||Stainless if Outdoors|
|Enclosure Rating||NEMA 12||NEMA 4X if Outdoors|
|Incoming Power Voltage||120VAC|
|Incoming Power Connection||Terminals|
|Incoming Power Disconnect||None|
|Incoming Power Short Circuit Protection||Circuit Breaker|
|Outgoing Power Loads||None|
|Motor Control||None||Start Signals to remote equipment|
|Ethernet Switch Power||24VDC|
|Operator Controls||Operator Interface|
|Field Connections||PLC Digital Inputs / Outputs
PLC Analog Inputs / Outputs